Vacker supplies swimming pool dehumidifiers and Spa dehumidifiers for hotels, homes, villas, commercial buildings, Olympic pools etc. Swimming pools and Spas generate a lot of humidity because the water from the pool is heated. Swimming pool dehumidifiers are used for such purposes. There is a difference in temperature between the water and air. This also causes higher humidity in the area. The heated air generates moisture and is released into the air. Indoor swimming pools and basement dehumidifiers especially are a big menace.
This causes huge humidity in the area which is very harmful. Hence, the surrounding air must be dehumidified properly. Properly selected swimming pool dehumidifier can reduce the humidity to normal levels.
How to reduce the humidity caused by indoor swimming pools and Spas?
Outdoor and indoor swimming pools generate excessive humidity. However, the problems are severe in indoor swimming pools. moisture is unable to find a way out and gets deposited everywhere including inaccessible areas. You can see moisture condensation on walls adjacent to the pool. This causes damage to paint, wooden doors & windows, metal doors & windows etc. Also, clothes, curtains, paintings etc. in the surrounding rooms will be affected. Mould formation happens on the walls and the upper layer of painting and cementing peels off.
In order to reduce the moisture from the air, you have to use a dehumidifier specifically designed for this purpose. Normal dehumidifiers are not suitable for this environment with high chlorine content. A swimming pool dehumidifier extracts moisture from the air and removes out of the pool area completely.
In addition to this, the swimming pools are treated with chlorine. Hence, the moisture in the water vapour is filled with chlorine particles. This adds to the woes of high humidity. This is detrimental to all articles around the pool.
Dehumidifiers for swimming pools and Spas
Swimming pool dehumidifiers are designed to solve the challenges of high humidity. They are multifunctional units which also provides heating of the air if required. This is the main difference of indoor pool dehumidifiers from normal industrial models. These dehumidifiers are entirely automatic and the humidity levels are controlled by a humidistat or hygrostat.
These automatic controls ensure that the swimming pool is in a wellcontrolled environment. The humidity and air temperature control results in a stabilized environment.
Our swimming pool dehumidifiers are designed in such a way that it uses very little energy for dehumidification and heating of the air. They recover the energy from the dehumidification process and are recycled to heat the air if required. These dehumidifiers are usually closedloop system with simple maintenance.
Calorex swimming pool dehumidifiers & Spa dehumidifiers
We are the authorized distributor for Calorex, UK (Part of Dantherm Group) swimming pool dehumidifiers, Spa dehumidifiers and associated heat pumps in the Middle East covering United Arab Emirates, Oman, Qatar, Saudi Arabia, Kuwait & Bahrain. Calorex is the world leader in swimming pool dehumidification technology. There are many models starting from a wallmounted pool dehumidifier to bigger models combined with pool heating equipment. Few of the models are listed below:
 Swimming Pool dehumidifier model DH15 having a capacity of 15 litres per day at 30°C.
 Pool dehumidifier model DH30 having a capacity of 30 litres per day at 30°C.
 Pool dehumidifier model DH60 of Calorex having a capacity of 60 litres per day at 30°C.
 Pool dehumidifier model DH75AX of Calorex having a capacity of 86 litres per day at 30°C. This is a floorstanding model.
 Pool dehumidifier model DH110AX of Calorex having a capacity of 108 litres per day at 30°C. This is a floorstanding model with single phase electricity connection.
 Pool dehumidifier model DH110BX of Calorex having a capacity of 108 litres per day at 30°C. This is a floorstanding model with a threephase electricity connection.
 Pool dehumidifier combined with heat pumps model AA 300 of Calorex with a capacity of 3.6 litres per hour.
 Pool dehumidifier combined with heat pumps model AA 300 of Calorex with a capacity of 4.5 litres per hour.
Dantherm Swimming pool heat recovery units and Dehumidifiers
We are the authorised distributor for Dantherm, Netherland (Part of Dantherm Group) swimming pool dehumidifiers and associated heat recovery units in the Middle East covering United Arab Emirates, Oman, Qatar, Saudi Arabia, Kuwait & Bahrain. Dantherm has multiple companies under its group, covering a wide range of swimming pool dehumidifiers. Few of the major models of Dantherm division are listed below:
 Dantherm Swimming pool dehumidifier model CDP40, having a capacity of 34 litres per day at 28°C. It has an airflow of 400 cubic meters per hour.
 DanthermSwimming pool dehumidifier model CDP40T, having a capacity of 34 litres per day at 28°C. It has an airflow of 400 cubic meters per hour. This is more silent than CDP40 at a sound level of only 43 dB(A).
 DanthermSwimming pool dehumidifier model CDP50, having a capacity of 52 litres per day at 28°C. It has an airflow of 680 cubic meters per hour.
 Dantherm Spa dehumidifier model CDP50T, having a capacity of 52 litres per day at 28°C. It has an airflow of 680 cubic meters per hour. This is more silent than CDP50 at a sound level of only 44 dB(A).
 Dantherm Spa dehumidifier model CDP70, having a capacity of 69 litres per day at 28°C. It has an airflow of 900 cubic meters per hour.
 Dantherm Spa dehumidifier model CDP70, having a capacity of 69 litres per day at 28°C. It has an airflow of 900 cubic meters per hour. This is more silent than CDP50 at a sound level of only 47 dB(A).
 Dantherm ducted swimming pool dehumidifier model CDP75, having a capacity of 74 litres per day at 28°C. It has an airflow of 1500 cubic meters per hour. These units are for direct connection into an air duct.
 Dantherm ducted swimming pool dehumidifier model CDP125, having a capacity of 124 litres per day at 28°C. It has an airflow of 2500 cubic meters per hour. These units are for direct connection into an air duct.
 Dantherm ducted swimming pool dehumidifier model CDP162, having a capacity of 164 litres per day at 28°C. It has an airflow of 3600 cubic meters per hour. These units are for direct connection into an air duct.
 Ducted high capacity pool dehumidifier model DanX AF is a pool hall ventilation heat pump. It has various models starting from a capacity of 13 litres per hour to 60 litres per hour at 28°C. The airflow capacity is from 4,850.00 cubic meters per hour to 24,000.00 cubic meters per hour. All of them work on 3 phase power supply.
 Dantherm pool air handling units with heat recovery models DanX 1XD, DanX 2XD & DanX 3XD. These models have a maximum air handling capacity from 1300 to 3500 cubic meter per hour. They have a dehumidification capacity ranging from 7 to 18 kg per hour.
 DanX XWPS Pool air handling units with heat recovery and heat pump. These are for very large swimming pools. The models in this range are 2/4 XWPS, 3/6 XWPS, 5/10 XWPS, 7/14 XWPS, 9/18 XWPS, 12/24 XWPS & 116/32 XWPS. The maximum air handling capacity varies from 4500 to 32000 cubic meter per hour. They have a dehumidification capacity ranging from 22 to 165 kg per hour.
 DanX HP series Pool air handling units with heat recovery and heat pump. The models in this range are DANX 1 HP, DANX 2 HP & DANX 3 HP. The maximum air handling capacity varies from 1300 to 3500 cubic meter per hour. They have a dehumidification capacity ranging from 7 to 18 kg per hour.
Models and specifications of swimming pool dehumidifiers
We are listing below, few of our major models of swimming pools dehumidifiers:

Swimming pool dehumidifier model VACDH75AX
The features and specification of this model of swimming pool dehumidifier are given below:
 It has a high moisture extraction capacity.
 The high capacity is achieved at low power consumption.
 The air grille is corrosionfree and easy to clean aluminium grille.
 The air filter and grill are easy to clean.
 The refrigerant complies to relevant standards with Zero ozonedepleting category refrigerant.
 The useful life of the dehumidifier is long since it has low internal operating pressures.
 The air outlet is adjustable.
 The twospeed centrifugal fans have quiet operation.
 The dehumidifier can work at lowtemperature upto5°C with its hot gas defrost.
 It has a remote humidistat and on/off function.
Applications of Swimming pool dehumidifier model VACDH75AX
 VACDH75AX model of swimming pool dehumidifier is suitable for indoor pools.
 Also, they are used in therapy pools.
 Health clubs and wellness centres can use these dehumidifiers to reduce humidity.
 Indoor spa pools in hotels and health clubs generate a huge amount of humidity, which can be reduced using VACDH75AX
Options available for Swimming pool dehumidifier model VACDH75AX
 We can provide a combined unit for fitting through the wall.
 Should you require, we can provide LPHW air heater complete with 3way valve and 12V thermostat interlock.
 If you require a 400V, 3phase option, please go for our model VACDH110.
Specifications Swimming pool dehumidifier model VACDH75AX
 Operating temperature range is 5 to 35 degrees Celsius.
 Dehumidification at 30 degrees Celsius, 60% relative humidity is 3.6 litres per hour.
 Heat recovered to air at 30 degrees Celsius, 60% relative humidity is 4.0 kilowatts.
 Airflow is 1180 cubic metre per hour.
 External static pressure is 0 Pa.
 Sound pressure level at 3 metres is 53dB(A).
 The refrigerant of VACDH75AX is R407c.
 The power supply is 230 Volt, Singlephase, 50 Hz.
 Nominal power consumption of 1.5 kilowatts.
 FLA of VACDH75AX is 9.5A.
 Maximum supply fuse for this swimming pool dehumidifier is 13A.
 LRA (compressor start) is 55A.
 Heater type of VACDH75AX is Optional LPHW.
 Heat output at 80 degrees Celsius flow is 8.9 kilowatts.
 Flow rate is 9.6 litres per minute.
 Product size (w x d x h) is 1520 x 385 x 796 millimetres.
 Weight of VACDH75AX is 143 kilograms.
 Condensate drain size (brass compression) is 15 millimetres.

Swimming pool dehumidifier model VACDH110AX
The features and specification of swimming pool dehumidifier model VACDH110AX are given below:
 It has a high moisture extraction capacity.
 The high capacity is achieved at low power consumption.
 The air grille is corrosionfree and easy to clean aluminium grille.
 The air filter and grill are easy to clean.
 The refrigerant complies to relevant standards with Zero ozonedepleting category refrigerant.
 The useful life of this swimming pool dehumidifier is long since it has low internal operating pressures.
 The air outlet is adjustable.
 The twospeed centrifugal fans have quiet operation.
 The dehumidifier can work at lowtemperature up to 5°C with its hot gas defrost.
 It has a remote humidistat and on/off function.
Applications of Swimming pool dehumidifier model VACDH110AX
 VACDH110AX model of swimming pool dehumidifier is suitable for indoor pools.
 Also, they are used in therapy pools.
 Health clubs and wellness centres can use these dehumidifiers to reduce humidity.
 Indoor spa pools in hotels and health clubs generate a huge amount of humidity, which can be reduced using VACDH110AX
Options available for Swimming pool dehumidifier model VACDH110AX
 We can provide a combined unit for fitting through the wall.
 Should you require, we can provide LPHW air heater complete with 3way valve and 12V thermostat interlock.
 We can supply a 400V, 3phase option.
Specifications Swimming pool dehumidifier model VACDH110AX
 Operating temperature range is 5 to 35 degrees Celsius.
 Dehumidification at 30 degrees Celsius, 60% relative humidity is 4.5 litres per hour.
 Heat recovered to air at 30 degrees Celsius, 60% relative humidity is 5.2 kilowatts.
 Airflow is 1180 cubic metre per hour.
 External static pressure is 0Pa.
 Sound pressure level at 3 metres is 53dB(A).
 The refrigerant of VACDH110AX is R407c.
 The power supply is 230 Volt, Singlephase, 50 Hz.
 Nominal power consumption of 2.1 kilowatts.
 FLA of VACDH110AX is 12A.
 Maximum supply fuse 20A.
 LRA (compressor start) is 66A.
 Heater type of VACDH110AX is Optional LPHW.
 Heat output at 80 degrees Celsius flow is 8.9 kilowatts.
 Flow rate is 9.6 litres per minute.
 Product size (w x d x h) is 1520 x 385 x 796 millimetres.
 Weight of VACDH110AX is 144 kilograms.
 Condensate drain size (brass compression) is 15 millimetres.

Swimming pool dehumidifier model VACDH33
This is a wallmounted type of swimming pool for low and medium capacity applications.
Features of swimming pool VACDH33
 It has a high humidity extraction ability with low energy consumption.
 It has zero ozonedepleting refrigerant.
 Because of low internal operating pressures, it has a long useful life.
 It may be in a cycle of fans or ongoing mode.
 The air outlet is adjustable to horizontal or vertical.
 The defrosting by hot gas allows operation at an air temperature of 5 ° C.
 There are many flexible installation options available.
 It has an on / off feature and a remote humidistat.
Options of swimming pool VACDH33
 We can provide a combined unit for fitting through the wall.
 Should you require, we can provide LPHW air heater
 An optional air filter can be supplied.
 If you want to keep the dehumidifier on the floor, we can supply a floor stand kit.
Specifications of swimming pool VACDH33
 Operating temperature range is 5 to 35 degrees Celsius.
 Dehumidification at 30 degrees Celsius, 60% relative humidity is 1.25 litres per hour.
 Heat covered to air at 30 degrees Celsius, 60% relative humidity is 1.9 kilowatt.
 Airflow is 440 cubic metre per hour.
 External static pressure is 0Pa.
 Sound pressure level at 3 metres is 48dB(A).
 The refrigerant of VACDH33 is R407c.
 The power supply is 230 Volt, Singlephase, 50 Hz.
 Nominal power consumption is 0.75 kilowatt.
 FLA of VACDH33 is 4.4A.
 Maximum supply fuse is 10A.
 LRA (compressor start) is 15A.
 Heater type of VACDH33 is Optional LPHW.
 Heat output at 80 degrees Celsius flow is 3 kilowatt.
 Flow rate is 5 litres per minute.
 Product size (w x d x h) is 780 x 255 x 653 millimetres.
 Weight of VACDH33 is 37 kilograms.
 Condensate drain size (flexible plastic hose) is 16 millimetres.

Swimming pool dehumidifier, ducted type, model VACAA500
This is a ducted type dehumidifier for indoor pools, therapy pools, Spa, health clubs, wellness centres, hotels etc.
Features of ducted type dehumidifier for pools, model VACAA500
 With the ducted type dehumidifier, you can efficiently dehumidify the entire pool hall.
 Ducted type dehumidifier for pools, model VACAA500 has a dynamic heat recovery pump.
 It has a constant twospeed flow fan.
 It has a 1.8 m lead remote control panel (12V), optionally with a 10meter cable.
 LPHW Air models of ducted type dehumidifier for pools, model VACAA500 have integral LPHW heat exchanger for air heating
 LPHW Air+Water models have integral LPHW heat exchangers for pool and air.
Specifications of ducted type dehumidifier for pools, model VACAA500
 The airflow of ducted type dehumidifier for pools, model VACAA500 is 1800 ± 10% cubic metre per hour.
 External available static pressure is 250Pa.
 Dehumidification of ducted type dehumidifier for pools, model VACAA500 at 30 degrees Celsius, 60% relative humidity is 4.5 litres per hour.
 Heat to air via heat pump is 6.1 kilowatt.
 Heat to air via LPHW (LPHW air models) is 7.5 kilowatt.
 Total heat to air (heat pump + LPHW) is 11.7 kilowatt.
 Heat to water via LPHW (LPHW Air + Water models) is 9.5 kilowatt.
 Product size (h x w x d) is 850 x 1027 x 730 millimetres.
 Weight of VACAA500 is 111 kilograms.

Swimming pool dehumidifier model VACDH55
Technical details of model VACDH55 are explained below:
 Operating temperature range is 5 to 35 degrees Celsius.
 Dehumidification at 30 degrees Celsius, 60% relative humidity is 2.5 litres per hour.
 Heat covered to air at 30 degrees Celsius, 60% relative humidity is 3.5 kilowatt.
 Airflow is 740 cubic metre per hour.
 External static pressure is 0Pa.
 Sound pressure level at 3 metres is 48dB(A).
 The refrigerant of VACDH55 is R407c.
 The power supply is 230 Volt, Singlephase, 50 Hz.
 Nominal power consumption is 1.2 kilowatt.
 FLA of VACDH55 is 7.5A.
 Maximum supply fuse is 13A.
 LRA (compressor start) is 30A.
 Heater type of VACDH55 is Optional LPHW.
 Heat output at 80 degrees Celsius flow is 5 kilowatt.
 Flow rate is 5 litres per minute.
 Product size (w x d x h) is 1245 x 255 x 653 millimetres.
 Weight of VACDH55 is 58 kilograms.
 Condensate drain size (flexible plastic hose) is 16 millimetres.

Swimming pool dehumidifier model VACCDP40
 Operating temperature range is 10 to 36 degrees Celsius.
 Operating humidity range is 40100% relative humidity.
 Dehumidification at 28 degrees Celsius, 60% relative humidity is 34 litres per 24 hours.
 Airflow is 400 cubic metre per hour.
 The sound pressure level is 46dB(A).
 The power supply is 230 Volt, Singlephase, 50 Hz.
 Product size (h x w x d) is 770 x 1010 x 326 millimetres.
 Weight of VACCDP40 is 56.5 kilograms.

Swimming pool dehumidifier model VACCDP40(T)
 Operating temperature range is 10 to 36 degrees Celsius.
 Operating humidity range is 40100% relative humidity.
 Dehumidification at 28 degrees Celsius, 60% relative humidity is 34 litres per 24 hours.
 Airflow is 400 cubic metre per hour.
 The sound pressure level is 43dB(A).
 The power supply is 230 Volt, Singlephase, 50 Hz.
 Product size (h x w x d) is 700 x 998 x 304 millimetres.
 Weight of VACCDP40(T) is 57.5 kilograms.

Swimming pool dehumidifier model VACCDP50
 Operating temperature range is 10 to 36 degrees Celsius.
 Operating humidity range is 40100% relative humidity.
 Dehumidification at 28 degrees Celsius, 60% relative humidity is 52 litres per 24 hours.
 Airflow is 680 cubic metre per hour.
 The sound pressure level is 47dB(A).
 The power supply is 230 Volt, Singlephase, 50 Hz.
 Product size (h x w x d) is 700 x 1160 x 326 millimetres.
 Weight of VACCDP50 is 65.0 kilograms.

Swimming pool dehumidifier model VACCDP50(T)
 Operating temperature range is 10 to 36 degrees Celsius.
 Operating humidity range is 40100% relative humidity.
 Dehumidification at 28 degrees Celsius, 60% relative humidity is 52 litres per 24 hours.
 Airflow is 680 cubic metre per hour.
 The sound pressure level is 44dB(A).
 The power supply is 230 Volt, Singlephase, 50 Hz.
 Product size (h x w x d) is 770 x 1148 x 304 millimetres.
 Weight of VACCDP50(T) is 66.0 kilograms.

Spa dehumidifier model VACCDP70
 Operating temperature range is 10 to 36 degrees Celsius.
 Operating humidity range of this Spa dehumidifier is 40100% relative humidity.
 Dehumidification at 28 degrees Celsius, 60% relative humidity is 69 litres per 24 hours.
 The airflow of this Spa dehumidifier is 900 cubic metre per hour.
 The sound pressure level is 50dB(A).
 The power supply of this Spa dehumidifier is 230 Volt, Singlephase, 50 Hz.
 Product size (h x w x d) is 770 x 1495 x 326 millimetres.
 Weight of this Spa dehumidifier model VACCDP70 is 75.5 kilograms.

Spa pool dehumidifier model VACCDP70(T)
 Operating temperature range of this Spa dehumidifier is 10 to 36 degrees Celsius.
 Operating humidity range is 40100% relative humidity.
 Dehumidification of this Spa dehumidifier at 28 degrees Celsius, 60% relative humidity is 69 litres per 24 hours.
 Airflow is 900 cubic metre per hour.
 The sound pressure level of this Spa dehumidifier model VACCDP70T is 47dB(A).
 The power supply is 230 Volt, Singlephase, 50 Hz.
 Product size (h x w x d) is 700 x 1483 x 304 millimetres.
 Weight of Spa dehumidifier model VACCDP70(T) is 77.5 kilograms.

High Capacity, Roofmounted dehumidifier for swimming pool; model VACDANX5/10s AF
 Dehumidification at 28 degrees Celsius, 60% relative humidity is 25 litres per hour.
 Operating temperature range is 22 to 36 degrees Celsius.
 Operating humidity is 5080%.
 Airflow is 9500 cubic metre per hour.
 External duct pressure is 300Pa.
 Outdoor air of VAC5/10sAF is 030%.
 The power supply is 400 Volt, Threephase, 50 Hz.
 power consumption is 16.1 kilowatt.
 Height is 1115 millimetres.
 Width is 3380 millimetres.
 Depth is 1400 millimetres.
 Weight of VAC5/10sAF is 800 kilograms.

High Capacity, Roofmounted dehumidifier for swimming pool; model VACDANX7/14s AF
 Dehumidification at 28 degrees Celsius, 60% relative humidity is 39 litres per hour.
 Operating temperature range is 22 to 36 degrees Celsius.
 Operating humidity is 5080%.
 Airflow is 14000 cubic metre per hour.
 External duct pressure is 300Pa.
 Outdoor air of VAC7/14sAF is 030%.
 The power supply is 400 Volt, Threephase, 50 Hz.
 power consumption is 24.1 kilowatt.
 Height is 1195 millimetres.
 Width is 3350 millimetres.
 Depth is 1900 millimetres.
 Weight of VAC7/14sAF is 1200 kilograms.

Swimming pool dehumidifier model VACDS51
This model is one of our biggest dehumidifier for swimming pools having a capacity of 84 litres per day. Major parameters are listed below:
 The unit has a dehumidification capacity of 84 litres per day at 30 °C & 80 % RH.
 The unit has a dehumidification capacity of 36 litres per day at 20°C & 60 % RH.
 Air volume capacity is 740 m³/hour.
 The machine can operate at an ambient temperature of 15°C to 35°C and humidity range from 30% to 90%.
 Electrical operating voltage is 230 Volta AC, 50 Hz.
 Current consumption is 6 Ampere and Maximum power input 0.98 kW.
Indoor swimming pool dehumidifiers
All of our indoor pool dehumidifiers can also be used for external pools. However, the calculation for indoor pool dehumidifiers will be entirely different. For indoor pools, the area is enclosed. Hence, the air volume is considered for the enclosed area.
Outdoor swimming pool dehumidifier
For outdoor pools, the unit will be working in continuous mode since the air will be continuously exchanged. In both cases, the dehumidifier is installed on the wall and water is drained out. The effectiveness of a dehumidifier for an outdoor pool is limited. The reason is that for an outdoor pool is open to the outdoor air and hence no control of the air intake. However, if you have any particular items or area to protect from high humidity, you may place a dehumidifier near to this area.
The principle of pool dehumidifier
These are condensation type dehumidifiers, which convert moisture into the water. There are condensation coils which cool down the air and absorbs the moisture content. This moisture is converted into water. A drain pipe has to be connected to drain out the water.
In the Middle East, we supply swimming pool & Spa dehumidifiers in the United Arab Emirates, Kingdom of Saudi Arabia, Oman, Qatar, Bahrain, Iraq, Lebanon, Syria, Egypt, Jordan, Libya, Tunisia, etc.
In Africa, we supply swimming pool& Spadehumidifiers in countries including Kenya, Algeria, Tanzania, Djibouti, Chad, Ghana, Rwanda, Uganda, Nigeria, Ethiopia, Morocco, Angola, South Africa, etc.
Also, we supply swimming pool& Spa dehumidifiers in India, Bangladesh, Pakistan, Afghanistan, Kazakhstan, Srilanka, Maldives, and Cyprus.