These units are pool air handling units combined with dehumidification, heat recovery and heat pump for swimming pools. They are manufactured by Calorex, UK.
Models of Pool air handling units with dehumidification, heat recovery and heat pump
Few of our major models, their features and specifications are listed below.
Features and specifications of VACDANXHP series
Features of Pool air handling units with dehumidification, heat recovery and heat pump (Model VACDANXHP series) are listed below
 These pool air handling units combined with dehumidification, heat recovery and heat pump have a builtin heat pump with elevated COP and rotating compressor.
 These models have optional watercooled condenser builtin for the pool or domestic water heating.
 It has a userfriendly control system builtin to manage highquality demand.
 These pool air handling units combined with dehumidification, heat recovery and heat pump have features for automatic temperature and humidity tracking and control in the pool hall.
 They have double crossflow heat exchangers with more than 85% high effectiveness and a small pressure drop.
 It has a builtin bypass for free cooling during summertime.
 These pool air handling units combined with dehumidification, heat recovery and heat pump have low power consumption due to highly efficient plug fans.
 It has compact F5/F7 highly effective filters with big surface area and lowpressure drop.
 It has a selfbearing cabinet with galvanized hotdip, powderpainted sandwich panels with 50 mm mineral wool insulation, 30 mm inner partition walls and adjustable feet bottom frame.
 The full cabinet and inner elements are specifically intended to resist the aggressive swimming pool environment as per Corrosion class C4 by EN / ISO 12944 2.
 This is achieved through an epoxy coated crossflow heat exchanger, aluminium frame coils, precoated fins and epoxy coating with all specially protected fasteners, bolts and nuts.
 For easy access for service, it has two large inspection doors with strong hinges and tongue locks and handles.
 With all sensors and electrical elements already linked, it has allinone box alternatives for simple and fast installation.
 It can communicate with the Building Management System (BMS) through either Modbus or BACnet.

Specifications of pool air handling units combined with dehumidification, heat recovery and heat pump; Model VACDANX1HP
 Nominal air volume is 1000 cubic metre per hour.
 Air volume is 1300 cubic metre per hour.
 External duct pressure of these pool air handling units combined with dehumidification, heat recovery and heat pump at nominal air volume is 350Pa.
 Outdoor air volume is 0100%.
 Dehumidification capacity recirculation at 30 degrees Celsius, 54% indoor is 1.7 kilograms per hour.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 7 kilograms per hour.
 Power consumption compressor at 30 degrees Celsius, 54% indoor is 0.6 kilowatt.
 Total power consumption of these pool air handling units combined with dehumidification, heat recovery and heat pump are 1.7 kilowatts.
 The power supply is 230 Volt, Singlephase, 50 Hz.
 Product size (h x w x d) is 1570 x 1750 x 515 millimetres.
 Weight of VACDANX1HP is 279 kilograms.

Specifications of pool air handling units combined with dehumidification, heat recovery and heat pump; Model VACDANX2HP
 Nominal air volume is 1750 cubic metre per hour.
 The air volume of these pool air handling units combined with dehumidification, heat recovery and heat pump is 2100 cubic metre per hour.
 External duct pressure at nominal air volume is 350Pa.
 Outdoor air volume is 0100%.
 Dehumidification capacity recirculation at 30 degrees Celsius, 54% indoor is 5.0 kilograms per hour.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 11 kilograms per hour.
 Power consumption compressor at 30 degrees Celsius, 54% indoor is 1.2 kilowatt.
 Total power consumption is 2.9 kilowatt.
 The power supply of this pool air handling units combined with dehumidification, heat recovery and heat pump is 400 Volt, Twophase, 50 Hz.
 Product size of this pool air handling units combined with dehumidification, heat recovery and heat pump (h x w x d) is 1570 x 1750 x 780 millimetres.
 Weight of VACDANX2HP is 379 kilograms.

Specifications of pool air handling units combined with dehumidification, heat recovery and heat pump; Model VACDANX3HP
 The nominal air volume of this pool air handling units combined with dehumidification, heat recovery and heat pump is 2750 cubic metre per hour.
 Air volume is 3500 cubic metre per hour.
 External duct pressure of this pool air handling units combined with dehumidification, heat recovery and heat pump at nominal air volume is 350Pa.
 Outdoor air volume is 0100%.
 Dehumidification capacity recirculation at 30 degrees Celsius, 54% indoor is 7.0 kilograms per hour.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 18 kilograms per hour.
 Power consumption compressor at 30 degrees Celsius, 54% indoor is 1.9 kilowatt.
 Total power consumption is 4.6 kilowatt.
 The power supply of this pool air handling units combined with dehumidification, heat recovery and heat pump is 400 Volt, Twophase, 50 Hz.
 Product size (h x w x d) is 1990 x 2250 x 890 millimetres.
 Weight of VACDANX3HP is 500 kilograms.
Features of VACDANXXWPS and VACDANXXWPRS
Features of Pool air handling units with dehumidification, heat recovery and heat pump (Model VACDANXXWPS and VACDANXXWPRS series) are listed below:
 It has an integrated heat pump with elevated COP and scroll compressor.
 It has optional watercooled builtin condenser for the pool or domestic water heating.
 It has a userfriendly control system for the management of highquality demand.
 It has automatic pool hall temperature and humidity tracking and control.
 They have a high effectiveness crossflow thermal exchanger of more than 75% and a small pressure fall.
 It has a builtin bypass for free cooling during summertime.
 It has a reversible heat pump (DanX XWPRS) with the option of active cooling during the summer.
 It has low power consumption due to highly efficient EC plug fans.
 It has highly efficient F5/F7 filters with a big surface area and lowpressure drop.
 It has loadbearing frame construction module with galvanized hotdip, powderpainted sandwich panels with 50 mm mineral wool insulation, 30 mm inner partition walls and adjustable feet bottom frame.
 All modules and inner elements are intended specifically to resist the aggressive swimming pool environment as per Corrosion class C4 according to EN / ISO 129442.
 They have an epoxycoated crossflow heat exchanger, aluminium frame coils, prepainted fins and epoxy coating with all specially protected fasteners, bolts and nuts.
 It has specially intended IP 66 damper engines for the swimming pool setting.
 For easy access for service, it has large inspection doors with strong hinges and tongue locks and handles.
 With a modular unit for simple and fast installation already linked to all sensors and electrical elements.
 For a fast electrical connection between unit and panel, it has a distinct control panel equipped with wires and plugs.
 They can communicate with the Building Management System (BMS) through either Modbus or BACnet.

Specifications of pool air handling units combined with dehumidification, heat recovery and heat pump Model VACDANX2/4XWPS
 Nominal air volume is 3350 cubic metre per hour.
 air volume is 4500 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity recirculation at 30 degrees Celsius, 54% indoor is 10.1 kilograms per hour.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 22 kilograms per hour.
 power consumption compressor is 4.4 kilowatt.
 total power consumption at nominal air volume is 7.4 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC2/4XWPS is 1660 millimetres.
 Width of VAC2/4XWPS is 3665 millimetres.
 Depth of VAC2/4XWPS is 880 millimetres.
 Weight of VAC2/4XWPS is 1150 kilograms.

Specifications of pool air handling units combined with dehumidification, heat recovery and heat pump; Model VACDANXAC3/6XWPS
 Nominal air volume is 4500 cubic metre per hour.
 air volume is 6000 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity recirculation at 30 degrees Celsius, 54% indoor is 16.2 kilograms per hour.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 29 kilograms per hour.
 power consumption compressor is 5.7 kilowatt.
 total power consumption at nominal air volume is 10.1 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC3/6XWPS is 1960 millimetres.
 Width of VAC3/6XWPS is 4135 millimetres.
 Depth of VAC3/6XWPS is 880 millimetres.
 Weight of VAC3/6XWPS is 1300 kilograms.

Specifications of pool air handling units combined with dehumidification, heat recovery and heat pump; Model VACDANXAC5/10XWPS
 Nominal air volume is 8400 cubic metre per hour.
 air volume is 10000 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity recirculation at 30 degrees Celsius, 54% indoor is 25.6 kilograms per hour.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 54 kilograms per hour.
 power consumption compressor is 8.8 kilowatt.
 total power consumption at nominal air volume is 16.8 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC5/10XWPS is 1960 millimetres.
 Width of VAC5/10XWPS is 4135 millimetres.
 Depth of VAC5/10XWPS is 1400 millimetres.
 Weight of VAC5/10XWPS is 1800 kilograms.

Specifications of pool air handling units combined with dehumidification, heat recovery and heat pump; Model VACDANXAC7/14XWPS
 Nominal air volume is 12500 cubic metre per hour.
 air volume is 14000 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity recirculation at 30 degrees Celsius, 54% indoor is 33.9 kilograms per hour.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 81 kilograms per hour.
 power consumption compressor is 12.0 kilowatt.
 total power consumption at nominal air volume is 23.0 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC7/14XWPS is 2120 millimetres.
 Width of VAC7/14XWPS is 4275 millimetres.
 Depth of VAC7/14XWPS is 1900 millimetres.
 Weight of VAC7/14XWPS is 2300 kilograms.

Specifications of pool air handling units combined with dehumidification, heat recovery and heat pump; Model VACDANXAC9/18XWPS
 Nominal air volume is 15500 cubic metre per hour.
 air volume is 20000 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity recirculation at 30 degrees Celsius, 54% indoor is 44.5 kilograms per hour.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 100 kilograms per hour.
 power consumption compressor is 16.0 kilowatt.
 total power consumption at nominal air volume is 31.0 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC9/18XWPS is 2250 millimetres.
 Width of VAC9/18XWPS is 4660 millimetres.
 Depth of VAC9/18XWPS is 1800 millimetres.
 Weight of VAC9/18XWPS is 2700 kilograms.

Specifications of pool air handling units combined with dehumidification, heat recovery and heat pump; Model VACDANXAC12/24XWPS
 Nominal air volume is 21500 cubic metre per hour.
 air volume is 26000 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity recirculation at 30 degrees Celsius, 54% indoor is 65.4 kilograms per hour.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 139 kilograms per hour.
 power consumption compressor is 24.0 kilowatt.
 total power consumption at nominal air volume is 46.0 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC12/24XWPS is 2760 millimetres.
 Width of VAC12/24XWPS is 4950 millimetres.
 Depth of VAC12/24XWPS is 2200 millimetres.
 Weight of VAC12/24XWPS is 3650 kilograms.

Specifications of pool air handling units combined with dehumidification, heat recovery and heat pump; Model DANXVACAC16/32XWPS
 Nominal air volume is 25500 cubic metre per hour.
 air volume is 32000 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity recirculation at 30 degrees Celsius, 54% indoor is 77.9 kilograms per hour.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 165 kilograms per hour.
 power consumption compressor is 30.0 kilowatt.
 total power consumption at nominal air volume is 60.0 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC16/32XWPS is 3010 millimetres.
 Width of VAC16/32XWPS is 5868 millimetres.
 Depth of VAC16/32XWPS is 2200 millimetres.
 Weight of VAC16/32XWPS is 4600 kilograms.