We are supplying Calorex make Pool air handling units with heat recovery for all types of swimming pools such as Olympic pools, hotel pools, villa pools etc.
Models of Pool air handling units with heat recovery
We have VACDANXXD and VACXKS series of models for all types of swimming pools.
Features of pool air handling units with heat recovery model VACXKS
 It has a userfriendly control system for the management of highquality demand.
 With automatic pool hall temperature and humidity tracking and control.
 It has a highefficiency crossflow thermal exchanger of more than 75% and a small pressure fall.
 It has a builtin bypass for free cooling during summertime.
 It has low power consumption due to highly efficient EC plug fans.
 It has highly efficient F5/F7 filters with a big surface area and lowpressure drop.
 With loadbearing frame construction module with galvanized hotdip, powderpainted sandwich panels with 50 mm mineral wool insulation, 30 mm inner partition walls and adjustable feet at the bottom frame.
 All modules and inner elements are specifically intended to resist the aggressive swimming pool environment (Corrosion class C4 as per EN / ISO 129442), with epoxycoated crossflow heat exchanger, aluminium frame heating coil, precoated fins and epoxy coating with all specially protected fasteners, bolts and nuts.
 Specially intended for swimming pool set with IP 66 damper engines.
 For easy access for service, it has large inspection doors with strong hinges and tongue locks and handles.
 With all sensors and electrical elements already attached, it has a modular unit for simple and fast installation.
 For a fast electrical connection between unit and panel, it has a distinct control panel equipped with wires and plugs.
 It can connect to either Modbus or BACnet BMS communication.
Features of pool air handling units with heat recovery model VACDANXXD
 It has a userfriendly control system integrated to manage highquality demand.
 With automatic temperature and humidity tracking and control in the pool hall.
 With specially developed software that always discovers the most energyefficient way of running the device under various circumstances.
 It has a double crossflow heat exchanger with more than 85% high efficiency and a small pressure drop.
 It has a builtin bypass for free cooling during summertime.
 It has low power consumption due to highly efficient EC plug fans.
 With highefficiency compact F5/F7 filters with big surface area and lowpressure drop.
 It has a selfsupporting cabinet with galvanized hotdip, powderpainted sandwich panels with 50 mm mineral wool insulation, 30 mm inner partition walls and adjustable feet bottom frame.
 The entire cabinet and inner elements are specifically intended to resist the aggressive swimming pool environment (Corrosion class C4 by EN / ISO 129442), with epoxycoated crossflow heat exchanger, aluminium frame heating coil, prepainted fins and epoxy coating with all specially protected fasteners, bolts and nuts.
 For easy access for service, it has two large inspection doors with strong hinges and tongue locks and handles.
 Allinone box solutions with all sensors and electrical elements already linked for simple and fast installation.
 It has a facility for either Modbus or BACnet BMS communication.
Specifications of pool air handling units with heat recovery
Few of our major models are listed below.

Pool air handling units with heat recovery model VACDANX1XD
 Nominal air volume is 1000 cubic metre per hour.
 air volume is 1300 cubic metre per hour.
 external duct pressure at nominal air volume is 350Pa.
 Outdoor air volume is 0100%.
 Dehumidification capacity VDI 2089 at 30 degree Celsius, 50% indoor is 7 kilograms per hour.
 total power consumption is 1.1 kilowatt.
 The power supply is 230 Volt, Singlephase, 50 Hz.
 Product size (h x w x d) is 1570 x 1750 x 515 millimetres.
 Weight of VACDANX1XD is 254 kilograms.

Pool air handling units with heat recovery model VACDANX2XD
 Nominal air volume is 1750 cubic metre per hour.
 air volume is 2100 cubic metre per hour.
 external duct pressure at nominal air volume is 350Pa.
 Outdoor air volume is 0100%.
 Dehumidification capacity VDI 2089 at 30 degree Celsius, 50% indoor is 11 kilograms per hour.
 total power consumption is 1.2 kilowatt.
 The power supply is 400 Volt, Twophase, 50 Hz.
 Product size (h x w x d) is 1570 x 1750 x 780 millimetres.
 Weight of VACDANX2XD is 344 kilograms.

Pool air handling units with heat recovery model VACDANX3XD
 Nominal air volume is 2750 cubic metre per hour.
 air volume is 3500 cubic metre per hour.
 external duct pressure at nominal air volume is 350Pa.
 Outdoor air volume is 0100%.
 Dehumidification capacity VDI 2089 at 30 degree Celsius, 50% indoor is 18 kilograms per hour.
 total power consumption is 1.9 kilowatt.
 The power supply is 400 Volt, Twophase, 50 Hz.
 Product size (h x w x d) is 1990 x 2250 x 890 millimetres.
 Weight of VACDANX3XD is 465 kilograms.

Pool air handling units with heat recovery model VAC2/4XKS
 Nominal air volume is 3350 cubic metre per hour.
 air volume is 4500 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 22 kilograms per hour.
 total power consumption at nominal air volume is 2.2 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC2/4XKS is 1600 millimetres.
 Width of VAC2/4XKS is 3101 millimetres.
 Depth of VAC2/4XKS is 880 millimetres.
 Weight of VAC2/4XKS is 850 kilograms.

Pool air handling units with heat recovery model VAC3/6XKS
 Nominal air volume is 4500 cubic metre per hour.
 air volume is 6000 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 29 kilograms per hour.
 total power consumption at nominal air volume is 3.0 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC3/6XKS is 1960 millimetres.
 Width of VAC3/6XKS is 3572 millimetres.
 Depth of VAC3/6XKS is 880 millimetres.
 Weight of VAC3/6XKS is 925 kilograms.

Pool air handling units with heat recovery model VAC5/10XKS
 Nominal air volume is 8400 cubic metre per hour.
 air volume is 10000 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 54 kilograms per hour.
 total power consumption at nominal air volume is 6.0 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC5/10XKS is 1960 millimetres.
 Width of VAC5/10XKS is 3572 millimetres.
 Depth of VAC5/10XKS is 1400 millimetres.
 Weight of VAC5/10XKS is 1300 kilograms.

Pool air handling units with heat recovery model VAC7/14XKS
 Nominal air volume is 12500 cubic metre per hour.
 air volume is 14000 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 81 kilograms per hour.
 total power consumption at nominal air volume is 11.0 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC7/14XKS is 2120 millimetres.
 Width of VAC7/14XKS is 3712 millimetres.
 Depth of VAC7/14XKS is 1900 millimetres.
 Weight of VAC7/14XKS is 1675 kilograms.

Pool air handling units with heat recovery model VAC9/18XKS
 Nominal air volume is 15500 cubic metre per hour.
 air volume is 20000 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 100 kilograms per hour.
 total power consumption at nominal air volume is 15.0 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC9/18XKS is 2250 millimetres.
 Width of VAC9/18XKS is 4080 millimetres.
 Depth of VAC9/18XKS is 1800 millimetres.
 Weight of VAC9/18XKS is 1925 kilograms.

Pool air handling units with heat recovery model VAC12/24XKS
 Nominal air volume is 21500 cubic metre per hour.
 air volume is 26000 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 139 kilograms per hour.
 total power consumption at nominal air volume is 22.0 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC12/24XKS is 2760 millimetres.
 Width of VAC12/24XKS is 4270 millimetres.
 Depth of VAC12/24XKS is 2200 millimetres.
 Weight of VAC12/24XKS is 2550 kilograms.

Pool air handling units with heat recovery model VAC16/32XKS
 Nominal air volume is 25500 cubic metre per hour.
 air volume is 32000 cubic metre per hour.
 Outdoor air volume is 0100%.
 Dehumidification capacity VDI 2089 at 30 degrees Celsius, 54% indoor is 165 kilograms per hour.
 total power consumption at nominal air volume is 60.0 kilowatt.
 The power supply is 400 Volt, Threephase, 50 Hz.
 Height of VAC16/32XKS is 3010 millimetres.
 Width of VAC16/32XKS is 5100 millimetres.
 Depth of VAC16/32XKS is 2200 millimetres.
 Weight of VAC16/32XKS is 3300 kilograms.
In the Middle East, we serve the United Arab Emirates, Kingdom of Saudi Arabia, Oman, Qatar, Bahrain, Iraq, Lebanon, Syria, Egypt, Jordan, Libya, Tunisia etc.
In Africa, we serve countries including Kenya, Algeria, Tanzania, Djibouti, Chad, Ghana, Rwanda, Uganda, Nigeria, Ethiopia, Morocco, Angola, South Africa etc.
Also, we supply to India, Bangladesh, Pakistan, Afghanistan, Kazakhstan, Srilanka, Maldives and Cyprus.